Review by: W. C.
Work Description: Rewired one outlet on existing ground fault circuit. Also removed two old hard wired smoke detectors and installed two new smoke/CO detectors on the same circuit.
Comments: Larry and his assistant Peter were very fast and knowledgeable. They were fast to diagnose the problems, and were finished in a short period of time. Cleaned up when complete. They offered to fix any additional problems, but there weren't any others.
Review by: Steve
Comments: My experience with Larry Laba has been excellent. He's very prompt and his work is very satisfactory. His work is done by the book and to code and he does a great job. I've recommended him many times. I've never been unhappy with his price. I would definitely continue to use him.