Review by: G. P.
Work Description: analysed the power outage at outlets and light/fan switch. Finally found the problem in the circuit breaker.
Comments: It took him 1 hr 30 min. and I think the job would have cost me less if it was charged by the hour not the job. I think the mileage cost should have been incorporated in the "job cost" since in seems a bit high!